Office Mob: +8615524105871
Office Tel: +86-024-31931990
Office Fax: +86-024-22845391
Low Voltage Overhead Service Drop Cable can be produced whose construction is phase conductor with neutral bare conductor or phase conductor with insulated neutral conductor , etc. And we can still produce the cables according to the request of customers....Send Inquiry
Low Voltage Overhead Service Drop Cables Application
Self-supporting overhead cable bundle, applied for electric power distribution in low voltage metropolitan, suburban and rural networks, for public lighting and house connections. Laid on pillars, consoles and house fronts.
Low Voltage Overhead Service Drop Cables Standards
HRN HD 626 S1
DIN VDE 0276 part 626
Low Voltage Overhead Service Drop Cables Construction
●Phase conductor: round Al conductor, multi wire stranded compacted (RM), class 2 acc. to HRN HD 383, phase conductors are marked with longitudinal protrusions (one, two or three)
●Neutral (supporting) conductor: round conductor, multi wire stranded compacted (RM), class 2 acc. to HRN HD 383, of aluminium alloy
●Insulation: XLPE (cross-linked polyethylene, recent mark: PE-X) compound TIX-2 or TIX-5 acc. to HD 626 S1
●insulation colour: black
Low Voltage Overhead Service Drop Cables Technical data
●during installation: -5 °C
●operating temperature: -30 °C up to +80 °C
●at short circuit of max. 5 s: 130 °C
●Nominal voltage: U/U = 0,6/1 kV
●Test voltage: 4 kV
●Minimal inner bending radius: 12D
●Phase conductors and neutral conductor
Production flow of Low Voltage Overhead Service Drop Cable
1.What is your delivery date?
A:The delivery date is about 5-7 days after receipt of payment.
2.What are your payment terms?
A:30% deposit in advance and 70% balance before shipment.
3.Can you send free samples?
A:Yes, free samples are available; you just need to pay the shipping cost.
Our usual packaging ways for Low Voltage Overhead Service Drop Cable are as followings, OR it can be as customer's request.