Office Mob: +8618002480485
Office Tel: +86-024-31140175
Office Fax: +86-024-22845391
Equipment: A small pressure equipment with automatic temperature control, timing and multi specification tubular mold cavity.
Second, the rubber material: and the wire wire line of the same, and the amount of glue is higher than the material, vulcanization system slightly stronger.
Third, the operation method:
1. Set temperature and time according to the vulcanization system of rubber material
2, with the use of rubber ink thinner sassafras cleaning repair, especially in conjunction with the full treatment of the department.
3, according to the size of the gap cut the appropriate amount of plastic repair, attention can not be more or less,
4, will cut the plastic material plug in the gap, pay attention to the rubber material should not be higher than the circumference of the wire. 5, with high temperature-resistant PP belt package good. and placing it in a tubular cavity with a slightly smaller diameter than the wire, locking the upper and lower modes so that the fill position has a certain pressure.
Note that the mold cavity diameter is slightly smaller than the 0.1~0.2mm.
6, to be cured time to, remove products, such as a small amount of plastic overflow, with a sharp blade repair, and wipe with thinner.
Iv. Verification Methods: The right amount of air into the wire and placed in the water, see if there is no leakage phenomenon can be judged good or bad.